1-10KV aerial insulated cables are suitable for power distribution grid system with rated AC voltage of 1-10KV. For aerial fixed laying, it shall be taken into consideration to keep a certain distance between cable and tree， it is permitted to have frequent contacts between cable and tree when cable is in operation.
1. Rated voltage 0.6/1KV and 10KV;
2. Allowable long-term operating temperature for cable conductor: PVC insulation shall not exceed 70℃, high density PE insulation shall not exceed 75℃, while XLPE insulation shall not exceed 90℃;
3. During short circuit (max. duration no more than 5S), the highest temperature of cable: 160℃ for PVC insulation, 150℃ for high density PE insulation, and 250℃ for XLPE insulation;
4. The laying temperature for cables shall be no less than -20℃, otherwise, preheat the cables.
12 months from the date of delivery (can be adjusted according to user requirements)